The water treatment plant is designed for deep desalination of source water as per SanPiN 220.127.116.114-01 regulations.
The equipment is mounted on a frame made of anodized aluminum machine profile, equipped with anti-vibration supports.
Pipes of the water treatment unit are made of propylene; electrical communications are housed in polyamide corrugated pipes. Purified water exceeds category 1 regulations.
|Installation dimensions||not more than 1000х800х1800 mm|
|Average treated water production rate||not less than 1 m3|
|Storage tank volume||2.0 m3|
|Peak water flow from the storage tank||no more than 4.0 m3/h|
|Average drainage water consumption||no more than 0.8 m3/h|
|Lifetime before overhaul (treated water)||no less than 8000 m3|
|Assigned lifetime (purified water)||not less than 50000 m3|
|Raw water pressure at system inlet||0.2...0.6 MPa|
|Installed electrical capacity||no more than 4.0 kW|
|Dry weight||no more than 260 kg|
|Power supply||380V, 50Hz|
Parameters of water purification
|Indicators||Units of measurement||Normal value for 1 category|
|Hydrogen indicator||pH units||6.0 - 9.0|
|Residual chlorine surfactant||mg/dm3||1.7|
|Heavy metal ions (total)||mg/dm3||15|
|Chemical oxygen demand||mg/dm3||150|
|Electrical conductivity at 20°C||cm/m||2*10|