The installation is used to clear water from suspended solids, colloids, compounds of iron, manganese, copper, sulfur, phosphorus, hydrogen sulfide, organic substances, to remove dissolved salts, including hardness salts, to disinfect the water from bacteria and viruses.
A preservative dose of sodium hypochlorite is added into the purified water which enters into the storage tank of the consumer.
The installation is fully automated and does not require external user control.
|Unit dimensions||no more than 740x420x1500 mm|
|Capacity||no less than 140 l/h|
|Drainage water consumption||no more than 140 l/h|
|The pressure of the source water at the inlet to the installation||0.1...0.3 MPa|
|Lifetime before overhaul, m3 of treated water||not less than 2000 m3|
|Assigned lifetime, m3 of treated water||not less than 6000 m3|
|Power consumption||not more than 0.75 kW|
|Dry weight without backfill||no more than 40 kg|
|Backfill weight||no more than 25 kg|
|Power supply||220 V, 50 Hz|
Parameters of water purification
|Indicators||Unit of measurement||Source water||Purified water||Drinking water|