MO-140-05 water treatment system
WE MAKE WATER PURE
Reverse osmosis water treatment system for cottages:
- Pure drinking water complying with the highest standards.
- Designed for cottages.
- Invention of military enterprise.
- Durable design and simple maintenance.
- Ready solution.
MO-140-05 water treatment system, storage of water and water supply is designed for purification of water from open reservoirs and wells from suspensions, colloids, disinfection of bacteria and viruses, removal of iron, manganese, sulfur, phosphorous, compounds, organics, including oil products, as well as for water purification of dissolved salts, including hardness salts and delivery of the purified water under pressure to the customer's (the use of a pump station after the system is not required) The system may be used for water supply of houses with up to 12 people and consumption rate of 250 l/person a day. The MO-140-05 system is supplied as a ready solution including set of consumable materials.
Drainage waters of the system are nontoxic, and their water evacuation on a relief and in the natural reservoirs is admissible without additional treatment. The system is completely automated and does nor demand control from the user.
- Service and guarantee.
- Delivery around the world.
- 15 years of experience.
- Professional staff.
|Name of parameter||Value|
|Dimensions, mm, no more than||500х400х1500|
|Average productivity of purified water (at +8°С temperature of source water), m3/h, no less than||3300|
|Average consumption of drainage water, l/h, no more than||140|
|Pressure in source water path at the system input, MPa||0.05…0.20|
|Assigned resource, m3 of purified water, no less than||600|
|Weight (without water), kg, no more than||60|
|Power supply||220 V, 50 Hz|
|Power consumption, W, no more than||900|
|Ambient temperature for storage and operation, °С||+5…+40|
|Service life before overhaul, m3 of purified water, no less than||2000|
Parameters of water purification for MO-140 system
|Parameter, units||Source water||Purified water||Drinking water norms 126.96.36.1994-01|
|Turbidity by kaolin, mg/l||5||0||0.5|
|Total iron, mg/l||8.0||0.1||0.3|
|Sulfides (hydrogen sulfide), mg/l||0.01||0||0.003|
|Biochemical oxygen demand, mg O2/l||10.0||0.5||2|
|Total hardness, mg-equivalent/l||20||1.5||7.0|
|Total mineralization, mg/l||2,000||300||1,000|
|Bacteria (forming and non-forming spores), m.t./l||1*106||0||0|
|Viruses, plaque-forming unit/l||1*106||0||0|